HV or LV correction?
Posted 18 August 2006 - 11:04 PM
Any comments recommendations appreciated.
Posted 20 August 2006 - 09:19 PM
While the concept of a single installation at the point of supply is appealing, there are a number of considerations to look at.
- Price. I am not sure of the pricing of the MV gear at present, but expect that it may be a more expensive option than the LV correction.
- Correcting on the secondary side of the transformer will correct th load on the transformer and probably improve the effective capacity of the transformer substantially.
- MV correction may require a significant number of small steps to correct the whole plant and keep it within desirable limits.
- Resonance problems if the 11KV impedance is high and inductive.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
Posted 21 August 2006 - 04:17 AM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users