Hi ! I am Milind. I have two queries regarding Generators and PF.
1. Does a captive power plant, consisting of several generators ( GTG or DG ) in parallel, require power
factor correction ? I mean , if the plant PF is around 0.8, that should be OK, is it not ? Is there any
overwhelming need to apply PF capacitors to improve it further ?
2. Suppose , if above CPP is runing in parallel with grid supply, can I control generator excitation so that
almost all the kVARs required by the load are supplied by the generators and I do not import any kVARs
from the grid thereby maintaining grid PF to almost unity ? This way, I do not require any capcitors and
I do not pay any penalty due to poor PF of the grid.
Thanks a lot and regards,
Power Factor Corretion For Generator
No replies to this topic
1 user(s) are reading this topic
0 members, 1 guests, 0 anonymous users