Posted 06 July 2007 - 04:35 AM
Is it possible to install 690V softstarter on a 3.3kv 400kw motor for wood chipper application. For VFD, we used to install a step down transformer at the input of VFD, then at the output there was a sine wave filter and a step up tranformer afterwards. Is it possible to do the same way for a softstarter? Has anyone of you done this before?
Posted 06 July 2007 - 05:40 AM
Yes, you can use a step down transformer and a step up transformer. You do not need the sinewave filter, but why not just use a standard MV soft starter. I am sure it would be cheaper!!
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | LMP Software | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
Posted 06 July 2007 - 06:28 PM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users