Pfc For Flood Light
Posted 25 August 2007 - 12:46 PM
I have some confusion for calculating the active and reactive power. I have a flood light with ballast 400W, 220V, Cosф 0.45. I calculated a capacitor 44uf for PF improvement upto 0.96 but available capacitor was 50uf. first I checked the current of light before PFC was 3.4A. I connected the capacitor then checked and found the following;
Current in main line (from switch to light) = 2A
Current in out going cable from capacitor = 2.3A
Current at light terminals = 3.4A
I couldn’t understand that why the current difference? 2 + 2.3 = 4.3A but we have 3.4A at light terminals. how can we calculate these figures. I think I am missing some thing.
Posted 25 August 2007 - 09:26 PM
You can not add the currents together.
The current into the capacitor is at phase quadrature to a resistive current. It is a capacitive current.
The current into the lamp is a vector made up of resistive current, and inductive current.
The current in the supply is a combination of the resistive component of the lamp current and the inductive current of the ballast and the capacitive current of the capacitor.
If you break the lamp current down to ists resistive component and it's inductive component, then you can subtract the inductive component and the capacitive component to end up with a resultant reactive current. The you square the reactive current and square the resistive current, add these together and take the square root to get the supply current.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
Posted 27 August 2007 - 05:47 AM
Now we have the values of current Im=2A at main cable, Ic=2.4A at capacitor out put and Il=3.4A at lamp cable. How can we calculate the both currents Im and Ic while capacitor is 50uf?
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users