Pf And Generator Supply
Posted 17 November 2007 - 11:58 AM
Any clarification appreciated.
Posted 20 November 2007 - 09:13 AM
I would think that you would want the powerfactor correction connected when you are running on the generator supply in order to reduce the current loading on the generator. This will reduce the losses in the generator, but will not significantly reduce the fuel consumption.
I would strongly recommend however, that you disconnect the correction during the transition from main supply to generator supply, and from generator supply to main supply. The switching transients could result in a resonant system and very severe voltages during the transition.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users