Posted 27 December 2007 - 11:49 PM
What does " up sized " mean ? Does it mean larger current rating? the schematic shows the capacitor on the load side of the contactor , just as the motor is on the load side of the same contactor ; so, if anything, the current seen by the contactor will be less with the capacitor than without ???
Posted 29 December 2007 - 12:22 AM
Welcome to the forum.
When the contactor closes, it will have to carry the inrush to the motor plus the inrush current to the capacitors. The contactor will see a reduced steady state current when the motor is running, but the closing transient could be sufficient to damage the contacts, hence the rating should be increased.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users