Voltage Rating Of Vsd
Posted 15 January 2008 - 02:57 PM
now, my question is will a 40 hp 460 volts 60hz variable speed drive be suitable to be used in a place having 380volts 60 hz power supply to drive a 40 hp/380 volts motor.
I feel drive has to be derated by 17%.
Posted 15 January 2008 - 06:08 PM
There are two issues here.
1. Will the drive operate on 380 volt? and 2. what will the rating be.
1. Most modern drives operate all the electronics from a switch mode supply off the DC bus so there should bee no problem operating the electronics off the lower voltage except that the under voltage and over voltage trip settings will need to be altered. You would need to talk to the supplier about doing that.
2. The real rating of the drive is not power, it is current. When you reduce the supply voltage, the current will stay the same, so the power rating will drop by the same amount as the current.
If you are looking for a unit to operate on 380 volt 60Hz, you could use any drive designed for the European market. The 50 Hz or 60Hz on the input will make no difference to the operation of the drive.
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | LMP Software | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
Posted 16 January 2008 - 03:28 AM
Otherwise it is not advisable to operate the drive beyond the specified voltage range.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users