Analytical Or Field Studies Of Pf Correction Energy Savings
Posted 05 February 2008 - 12:04 AM
I have tried several times to find studies that document these small energy savings from pf correction, but so far, all I've been able to find is anecdotal. I'd really like to have a report based on a field study or maybe a theoretical study using a model of a typical electrical distribution system of a C&I facility. Such evidence would provide a firm foundation for combatting inaccurate energy savings claims. Does anyone know of any studies that could help?
Posted 05 February 2008 - 09:34 AM
The addition of power factor correction does save energy, there is no dispute about that, but it will not reduce the energy consumed by equipment connected to the supply. The energy saved is in the distribution equipment on the supply side of the power factor correction equipment.
If you apply power factor correction to your main switchboard, you will not see any savings on your supply meter unless there is a long cable between your meter and your main board.
Some sales people claim that energy (KWHrs) will be reduced significantly in the corrected plant and this is not true. The energy savings are in the distribution system and that is not metered at the consumers plant. Cost savings are based on power factor or KVA penalties.
In the distribution system, the addition of power factor correction not only reduces i2r losses in the cables and transformers, but it increases the utilization of transformer and generators. The transformer and alternator loading is based on current. (often expressed as KVA) If you have a load power factor of 0.5, the maximum KW loading on a transformer is halved. Correcting the power factor up to 1.0 would enable two time the KW loading on a transformer compared to it's maximum load at a power factor of 0.5 - This saves a lot of investment in distribution plant.
I do not have any case studies covering the savings in the distribution system, but it is easy to calculate what savings can be made provided that you know what the losses are.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
Posted 06 February 2008 - 12:03 AM
Posted 07 February 2008 - 03:42 AM
Look at table 2 on page 3. It shows that they implemented a $55,000.00 power factor improvement program, but list the energy savings as "N/A", meaning there was none. They do show cost savings and payback because they avoided a lot of penalties, but that had nothing to do with energy savings.
By the way, here is the results of my search at this site, there are some other interesting reads there.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users