Igbt Damaged In Ab Inverter
Posted 15 October 2009 - 05:42 AM
I had been working for re-programming an Allen Bradley 5.5kw inverter for running a 2.2kw motor. The inverter had been working with 5.5kw motor perfectly before re-programming. When I set all parameters and enabled the inverter, “Enabled” displayed on its HMI but motor did not start while I set 3.5HZ in “Minimum freq” parameter. After almost 5 sec, when inverter was enabled, its IGBT blasted like a bomb and ……..
My inverter is now dead. I was amazed how it could be possible. I have many times programmed the inverters but it happened first time in my 13years field life.
Any body has any idea for that problem?
Posted 15 October 2009 - 04:05 PM
Is the 2,2kW motor good at all (had it been checked, started on line and checked running before the connection to the VFD) ?
And maybe the circuit breaker intended for the previous 5,5kW motor was mistakenly used with the faulty 2,2kW one?
Posted 15 October 2009 - 05:50 PM
Have you checked the 2.2KW inverter?
I would suggest that there may be a problem with it.
At 3.5 Hz, if the shaft was not rotating, the motor could draw excessive current, especially if it has a fault and this coupled with poor inverter protection could be why the smoke came out.
I would check to see if you have the motor wired up correctly. A common fault here is to connect a 230/400 volt motor in delta for 400V operation when it should be connected in star.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
Posted 18 October 2009 - 04:47 PM
Normally when we enable the AB inverter “Enable” and frequency command display on its HMI. But in my case “Enable” displayed but no frequency command appeared and after 5sec, IGBT blasted and MCB tripped. Really first time I had seen that.
After that I rechecked the motor and all circuit and found every thing OK. I checked that motor with another inverter and found OK. This is possible that I made a mistake but what? If high current passed in inverter, why it did not trip?
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users