Posted 14 August 2010 - 08:04 AM
Posted 14 August 2010 - 10:19 PM
The major consideration is usually the voltage during run as any continuous voltage drop is power loss.
Commonly in Australia and New Zealand, the standards call for a maximum of 5% but many target 2% voltage drop during run.
The major concern with voltage drop during start is the effect on other equipment.
Most equipment designed to operate on a 50Hz supply can tolerate a minimum voltage of Vnom - 15%.
If we allow for a 3% drop in the line voltage (bottom end of allowable supply voltage, then you would want to restrict the voltage drop during start to 12%.
Note most motors starters are of areduced voltage type so voltage drop during start does not hame a negative impact on the motor unless you require full DOL torque at start.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users