Capacitor Current Harmonics And Its Limit
Posted 31 January 2011 - 05:09 PM
Posted 01 February 2011 - 07:34 AM
If the harmonic voltage is due to a distortec curent flowing in the load, then the addition of the capacitor will reduce the high frequency of the supply and can increase the harmonic current flowing in the load.
Most power factor correction capacitors have a maximum current rating of 110% of nominal. In ohter words, provided that the carmonic current (total) is less than 10% of the nominal current, there should not be an issue.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | AuCom | Soft Starters
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users