PF for Across line and VFD motors
Posted 16 February 2004 - 09:58 PM
Posted 22 February 2004 - 12:20 AM
Welcome to the forum.
Bulk correction will not normally cause problems in this situation. It is commonly applied, however I would strongly recommend that you install detuning reactors with the capacitors in order to reduce the harmonic current flow through the capacitors (causing heat and reducing the capacitor life) and also to reduce the supply transients as the capacitors are switched in and out of circuit.
For bulk correction, you need to use a controller to automatically switch the banks in and out of circuit as the load changes.
One note of caution, if the supply impedance is reasonably hgh or inductive, you can have supply resonance problems causing very high voltages on the supply. This can in turn result in damage to the SCRs used in soft starters. I would recommend using line contactors with the soft starters to minimise and damage.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | AuCom | Soft Starters
1 user(s) are reading this topic
0 members, 1 guests, 0 anonymous users