Soft Starter Upstream Pd
Posted 07 November 2011 - 11:28 PM
I have a water well pump being fed from a soft start panel. The motor is around 57kW so I estimate around 102A/phase. But wondering what the feeder pd should be. I'm reckoning on a 160A MCCB @ any helpers please
Posted 08 November 2011 - 08:27 AM
Th upstream protection MCCB or fuses must be sized to protect the cable used, so determine the cable size and then select the protective device to protect that cable.
The motor starter must include protection to protect the motor. This is a separate issue.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
1 user(s) are reading this topic
0 members, 1 guests, 0 anonymous users