caps arranged in wye vs delta
Posted 22 June 2005 - 06:59 PM
Posted 22 June 2005 - 07:36 PM
Welcome to the forum.
Capacitors can be wired in star or in delta, there is no difference to the supply. You m aust ensure that the appropriate values are use though as the star values are different to the delta values. (KVAR remains the same, but the uF changes)
You need to use higher voltage capacitors in delta connection than in star, check the cost differential.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | Soft Starters
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users