# Kontactors for star/delta

### #1

Posted 12 November 2005 - 11:54 PM

How can I define size of the contactor for star delta switch.

I have motor on the sit for 250 Kw I=465A.

I there any different in star and in delta.

### #2

Posted 13 November 2005 - 05:05 AM

### #3

Posted 15 November 2005 - 11:29 PM

I am firm believer that all electical equipment should be selected on the basis of motor nameplate Full Load Current and not just kW.

Based on that I would suggest the following.

Line Contactor: 270 Amps AC3

Delta Contactor: 270 Amps AC3

Star Point Contactor: 154 Amps AC3

Make sure that you use a dedicated star/delta timer ie a dedicated star/delta timer includes a inbuilt delay to ensure that the Star Point Contactor has de-energised and the arc has been fully extinguished before the Delta Contactor is energised. A standard timer does not provide this functionality and if used can result in the Delta contactor closing on a short and welding.

jraef, I am interested in your ptroposal of having a motor contactor with a 42% rating. Could you please explain that for us.

Regards,

GGOSS

### #4

Posted 16 November 2005 - 03:27 AM

Take a look at this drawing. In that configuration (sorry, US nomenclature), the 1M contactor is sized for 58%, but the 2M contactor needs only be sized for the remaining 42% technically.

http://www.ssusa.cc/reference/wiring_diagrams/standard_series_drawings/series_107/107_21.pdf

I was incorrect about the mechanical interlock however, that needs to go between 2M and S, not 1M and 2M, so it will almost always involve dissimilar contactor frame sizes. I was trying to o from memory, which is frequently faulty.

OK, I have edited this several times and can't get the BB code to ork right, so cut and paste into a browser window. Sorry.

### #5

Posted 16 November 2005 - 10:01 AM

Surely the current through the main contactor and the delta contactor are equal? both are carrying winding current so should be rated at 58% of the line current?

Star delta starters are foreign to the USA so we have to make allowances!!

Best regards,

Mark Empson | administrator

Skype Contact = markempson | phone +64 274 363 067

LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | AuCom | Soft Starters

### #6 Guest__*

Posted 16 November 2005 - 10:26 AM

With reference to Jraef's circuit:

1. Isolator

must be at least rated for motor line current In=465A.

2. Star contactor S (first to energize)

must be at least rated for motor line current divided by 3

or In/3 = 465/3 =155A.

3. Main contactor 1M (energizes after S)

rated for motor line current divided by square root of 3

i.e. In/1.73=270A

4. Delta contactor 2M (third to energize, S off)

rated for motor line current divided by square root of 3

i.e. In/1.73=270A

5. Overload OL

rated for motor line current divided by square root of 3

i.e. In/1.73=270A

6. type of contactor

AC3: applicable for starting and stopping squirrel-cage motors

### #7

Posted 16 November 2005 - 10:27 AM

*Originally posted by Anonymous*

Let me put these in formulae and be more specific.

With reference to Jraef's circuit:

1. Isolator

must be at least rated for motor line current In=465A.

2. Star contactor S (first to energize)

must be at least rated for motor line current divided by 3

or In/3 = 465/3 =155A.

3. Main contactor 1M (energizes after S)

rated for motor line current divided by square root of 3

i.e. In/1.73=270A

4. Delta contactor 2M (third to energize, S off)

rated for motor line current divided by square root of 3

i.e. In/1.73=270A

5. Overload OL

rated for motor line current divided by square root of 3

i.e. In/1.73=270A

6. type of contactor

AC3: applicable for starting and stopping squirrel-cage motors

#### 0 user(s) are reading this topic

0 members, 0 guests, 0 anonymous users