edogro Posted July 22, 2008 Report Share Posted July 22, 2008 can anyone tell me how to calculate the micro farads necessary to generate the capacitance to be added to a motor to increase PF to near unity? I know how to calculate kVAR and how to calculate how much it has to decrease in order to approach unity but I have been unable to find how to calculate the micro farad levels necessary to provide the capacitance. Thanks! Link to comment Share on other sites More sharing options...

marke Posted July 22, 2008 Report Share Posted July 22, 2008 Hello edogro Welcome to the forum. Power factor correction capacitors are rated in KVAR at a particular voltage and frequency, so it is not necessary to calculate the microfarads required. For a given capacitance, at a given voltage and frequency, the current through the capacitor can easily be calculated. If you then multiply the voltage across the capacitor by the current through it, you get the VAR of the capacitor. Divide this by one thousand, and you have the KVAR of the capacitor. You can calculate the current by the voltage divided by the reactance where the reactance is 1/(2 x pi x f x C). pi =3.142.... f = frequency C = capacitance. A bit of algebra and you can come up with the formula to calculate the capacitance from the KVAR. Note for a three phase capacitor, assume three equal capacitors star connected with phase - neutral voltage across the capacitor. If the final capacitor is made up of three delta connected capacitors, you can use star to delta transformation formulae to calculate the equivalent delta connected capacitors. Best regards, Mark Mark Empson | administratorSkype Contact = markempson | phone +64 274 363 067LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | AuCom | Soft Starters Link to comment Share on other sites More sharing options...

edogro Posted August 4, 2008 Author Report Share Posted August 4, 2008 Hello edogro Welcome to the forum. Power factor correction capacitors are rated in KVAR at a particular voltage and frequency, so it is not necessary to calculate the microfarads required. For a given capacitance, at a given voltage and frequency, the current through the capacitor can easily be calculated. If you then multiply the voltage across the capacitor by the current through it, you get the VAR of the capacitor. Divide this by one thousand, and you have the KVAR of the capacitor. You can calculate the current by the voltage divided by the reactance where the reactance is 1/(2 x pi x f x C). pi =3.142.... f = frequency C = capacitance. A bit of algebra and you can come up with the formula to calculate the capacitance from the KVAR. Note for a three phase capacitor, assume three equal capacitors star connected with phase - neutral voltage across the capacitor. If the final capacitor is made up of three delta connected capacitors, you can use star to delta transformation formulae to calculate the equivalent delta connected capacitors. Best regards, Mark Link to comment Share on other sites More sharing options...

edogro Posted August 4, 2008 Author Report Share Posted August 4, 2008 Hello Mark: Thanks for the reply, I will run some calculations and let you know how it works out. I am not sure I followed your explanation or if I understood correctly. If motor run capacitors connected in a delta configuration for power factor correction create a specific amount of KVAC to offset the KVAR of the installation, is determined by voltage and frequency across the capacitors how then is the total amount of capacitance effected by the size of the capacitors? You mentioned the star to delta formula, where can I find this? Best regards!! Link to comment Share on other sites More sharing options...

Sharon Posted January 2, 2010 Report Share Posted January 2, 2010 can anyone tell me how to calculate the micro farads necessary to generate the capacitance to be added to a motor to increase PF to near unity? I know how to calculate kVAR and how to calculate how much it has to decrease in order to approach unity but I have been unable to find how to calculate the micro farad levels necessary to provide the capacitance. Thanks! Thanks you for the post. Hi guys, Im a newbie. Nice to join this forum. Link to comment Share on other sites More sharing options...

Bysikmode Posted April 20, 2014 Report Share Posted April 20, 2014 What I read I really liked it. Thank you for your information! dubli Link to comment Share on other sites More sharing options...

Eurybates Posted June 11, 2014 Report Share Posted June 11, 2014 Really, If you don't agree with Mark, then the best thing to do is to find the inter-cable-phase-adapter, Make sure the termination is nice and tight. Swing on it a few times and go research the power triangle for a while before dedicating your life to three phase theory. If this does not work, then get a job talking as much *beep* your body can handle without imploding into approx. 10 micro-farads. Best of luck PS.. If this post is not deleted, I will assume that LMP forum is dead and gone. ) .. Was good talking Link to comment Share on other sites More sharing options...

marke Posted June 16, 2014 Report Share Posted June 16, 2014 Definitely not dead, just pounded by spam for a while and so filtered quite hard at present. BRMark Mark Empson | administratorSkype Contact = markempson | phone +64 274 363 067LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | AuCom | Soft Starters Link to comment Share on other sites More sharing options...

## Recommended Posts

## Create an account or sign in to comment

You need to be a member in order to leave a comment

## Create an account

Sign up for a new account in our community. It's easy!

Register a new account## Sign in

Already have an account? Sign in here.

Sign In Now