Posted 21 July 2004 - 10:39 PM
Is there a way to find ratings for multiple busbars,i.e. three
100x10 in parallel per phase, A) unenclosed
C) insulated for A) or above
Posted 01 August 2004 - 12:03 AM
There are numerous rules of thumb that have been applied in the industry for certain conditions, but the best thing to do, is to create the environment and make temperature rise measurements.
When putting busbars in parallel, it is necessary to derate to ensure that the current sharing imbalance does not cause overheating of one bar, or one point in a bar. I would normally derate by 10 - 20%. The amount of dertaing is also dependent on the spacing between the busbars. If they are very close, you will restrict the airflow between the bars and a greater derating will be required.
Mark Empson | administrator
Skype Contact = markempson | phone +64 274 363 067
LMPForum | Power Factor | L M Photonics Ltd | Empson family | Advanced Motor Control Ltd | Pressure Transducers | Smart Relay | GSM Control | Mark Empson Website | AuCom | Soft Starters
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users